Peter -suction LED lights, tear bead lamps, protective LEDs (lampshade materials: acrylic), downlight (reflector material aluminum), embedded milk white panel lamps (lampshade: 1. 4MMPMAA board anti -static treatment) Head lights (lampshades: tempered glass), open lamps, and other lamps. The thickness of the lamp shell is not less than 0.35mm, and it meets the thickness of different types of lamp steel.
All metal parts of the lighting lamps must be corrosive (except stainless steel), and paint two white anti -splicing roasted paint. All control devices, internal lines and wind back grooves (if) of the lighting lamps must be secretly installed in the lighting lamp.
Cantonic lamp socket: glaze, the socket has a bronze rotating shell and welding lead.
Legend/grille: Treaty prism: transparent mold injection, clean, dustered, and pure acrylic.
Piboderbon -type aluminum grille: pre -mirror -coated pre -oxygenized aluminum grille with semi -mirror, and the grille suppression molding with pressure particles horizontal plane as the plane. The grille connection has a tight accessories, and the striker slot structure does not allow light leakage.
Pangal plastic grid: vacuum metal polyethylene grille with mirror coating and antistatic protection.
The down reflective hood aluminum dioxide material shows the minimum halo and minimum reflex flash.
Lighting reflex surface coating: paint surface layer: static dry powder coated with the surface layer or porcelain glaze surface.
Mirror/semi -mirror coating: electrolytic glorious oxidation coating on aluminum grids and reflection surfaces.
Universal incandescent lamp: internal scrub.
Fluorescence: Three base colors, color temperature 5000K, RA ≥ 80.
Noise level: working current 430mA noise A, working current 800mA noise B, working current 1500mA noise D level, noise reaches D -level should beolate installation and insulation to reduce noise transmission.
The bonitizer adopts other special types of high -power factor, high -efficiency, full light output or lighting lamps. The adjacent ballasts should be separated in the lighting lamps to provide heat dissipation.
Electronic ballast: Using high -frequency electronic ballast (metal case), quickly start, the power factor is greater than equal to 0.98, and the total harmonic distortion is less than 10%.
Electronic lighting zone: compatible with the light and the lighting system, the smallest “full load-20%” lighting range.
HID ballast: High -power factor, with a constant Watter automatic transformer ballast with an original melting. Run-20 ° F is 108 ° F. Provide overheating protection for all human HID lighting fixtures.
Space -time switch, photoelectric device, control sensor, ceiling installation ultrasonic sensor (360 °), sunlight sensor, local lighting control, intelligent lighting control system:, concentration and some regional control management, and other controller classes.
Inspection ceiling form and cooperate with the lamps and attachments.
When the lamp weighs greater than 3kg, it is fixed on the bolt or embedded hook.
Soft wire chandeliers, the weight of the lamp is 0.5kg and below, the soft wire itself is lifted by itself, the lamps greater than 0.5kg use the hanging chain, and the soft wire editor is in the hanging chain to make the wires uncomfortable.
The fixation of the lamp should be firm and reliable, and must not use wooden wedges. The screws or bolts for each lamp are not less than 2; the diameter of the insulating table is 75mm and below. 1 screw or bolt is fixed.
The steel pipe is a lamps. The inner diameter of the steel pipe is not less than 10mm; the wall thickness of the steel pipe is not less than 1.5mm.
The lamps shall not be installed directly on the combustible matter; the high temperature of the lamp surface is close to the combustible materials, and measures such as heat insulation and heat dissipation should be taken.
Fixed lamps with electricity and providing insulating materials for anti -electrical shock, combustion and fire prevention.
The embedded lamps are neatly fixed to the surface of the installation, and no light or gap must be leaked. Install heat -resistant rubber pads if necessary.
The lamps installed in the ceiling are supported and fixed on the grid from two diagonal.
The lamps installed in the same room or place, the heart line deviation is not greater than 5mm, and the lamps must not be installed above the top of the high and low voltage power distribution equipment and naked mother line. Tall equipment must not be installed above the lamps. Do not use the lighting light to make a line box.
Pangal cone cover and grille and quartz light should be operated with new, clean white cloth or silk gloves, and must not be touched naked.
Explosion -proof lamps, shell protection levels, and temperature groups should be adapted to the hazardous environment of the explosion. The supporting facilities should be complete, and non -explosion -proof parts shall be used to replace the lamp accessories.
Outdoor lighting lamp electric pole base: The rivet on the base is at least 2 inches. Install the electric pole vertically and use double nuts to adjust.
The ground wire is connected to the ground rod and the lamp; otherwise, set the ground pole for each electric rod as the grounding wire.
Check whether the wires have mechanical damage and correct connection. The wire connector and terminal are tested. The wires are continuous and insulated testing, and each phase is correct. The lighting system is powered on, the lighting control should be consistent with the labeling of the lighting distribution box and the circuit, and the switch is corresponding to the order of the lighting control. The lighting system is 24h, and the lighting fixtures should be turned on. The operating status of the operation every 2H will be recorded. There is no failure within the trial operation time.
Note: The above tools should have CCC testing, certification and calibration. Defects such as lamps and its accessories are complete, no mechanical damage, deformation, paint peeling, and lampshade rupture.